2022-3-2 09:57| 发布者: steelfu4mo| 查看: 360| 评论: 0 |原作者: 佛山万庆物资
I believe that many customers when the inquiry will question, why the machine room wall board with color steel plate will be more expensive than the ordinary color steel plate price?
Because the color steel plate in the machine room is actually a composite material of the paint steel plate and the gypsum board, Standard machine room color steel plate shall be formed by double-sided galvanized steel plate with sufficient thickness T0.6, Then, after passing through the fully automatic pre-processing technology, High-voltage electrostatic powder spraying, Colors can be customized, spraying after the coating protection surface paint layer, An environmentally friendly two-component glue is combined with the gypsum board, Surface steel plates are made of pre-painted color steel rolls, This pre-painted plate paint is relatively thin, Only at 15~20um, scratch scratch ability and lasting corrosion resistance are relatively poor, Special incision site is prone to rust; Another important element is this pre-painted color steel plate, Look at the steel plate cut, The cut metal is exposed is the pre-painted color steel plate, The cut metal is rolled plate, Buy back directly processing molding and gypsum board composite.
机房专用彩钢板也叫单面石膏彩钢板，佛山市万庆物资有限公司所销售的机房墙板专用彩钢板采用的钢板基材是0.6mm热镀锌钢板，误差不超过20 um，正面烤漆厚度不小于20um，背面烤漆厚度不小于12um;内衬辅材采用法国拉法基12mm的石膏板。产品通过国家防火建筑材料质量监督检验中心120分钟的检验，GB∕T9978.1-2008《建筑构件耐火试验方法》第一部分：通用要求GB∕T 9978.8-2008 《建筑构件耐火试验方法》第八部分：非承重垂直分隔构件的特殊要求。能充分满足各种场所建设装修的防火要求。
Special color steel plate for the machine room is also called one-sided gypsum color steel plate, the steel plate sold by Foshan Wanqing Materials Co., Ltd. is 0.6mm hot galvanized steel plate with error not more than 20 um, front paint thickness not less than 20um, back paint thickness not less than 12um; the lining auxiliary material uses French 12mm gypsum plate.The product has passed 120 minutes of inspection by the National Fire Protection Building Materials Quality Supervision and Inspection Center, GB∕T9978.1-2008 Fire Resistance Test Method for Building Members Part 1: General Requirements GB T 9978.8-2008 Fire Resistance Test Method for Building Members Part 8: Special requirements for non-load-bearing vertical separation components.Can fully meet the fire prevention requirements of various site construction and decoration.
If you want to know more, you can search Foshan Wanqing Materials Co., Ltd. for one-to-one communication with technical consultants.Such as machine room color steel plate price, machine room color steel plate specifications and models and other more information, welcome to contact us at any time, sincerely invite to provide you with the most satisfactory service!